CJ1W-PRM21 Omron Automation and Safety Controllers CJ1 Profibus Master datasheet, inventory, & pricing. This article (NJ base) explains how to setup the configuration for the NJ with a CJ1W-PRM21 Profibus communication unit connecting. Buy Omron CJ1W Series PLC I/O Module, 31 x 90 x 68 mm CJ1W-PRM Browse our latest plc-i-o-modules offers. Free Next Day Delivery.
|Genre:||Health and Food|
|Published (Last):||1 March 2016|
|PDF File Size:||18.44 Mb|
|ePub File Size:||11.62 Mb|
|Price:||Free* [*Free Regsitration Required]|
But still I can’t scan in order to find connected slaves. Following DTM reported the error: Hello Daniel, Thanks for your answer. The number of bytes its going to recive and send.
But it’s possible that the problem is the hardware config. The module was update to firmware V3, but I have only in step 7 the product versions 1 and 2. I’ve made mistake, because communication module is diffirent than I mentioned before. Share this post Link to post Share on other sites. It supposed to be toolbus usb in configuration tab, and now i can use test, and go online options without cjw errors. Register a new account. I don’t have this software installed on pc I uploaded the file already.
Posted 21 March edited. I should do any thing else, Thaks.
Sign up for a new account in our community. If this is already done, it would be good to see how they have been configured. Hello Ariel; You seem to have had difficulty in uploading your diagnostic information.
Try to run the AutoUpdate so you’ll get a newer version if you have a registered copy. Started by malyalewariat18 March. It is profibus slave.
Here I have que diagnostic of the cp slave. I’ve set up correct connection parameters of cj1w-prm profibus master. What I can do. Sign In Sign Up. All about Decentral Peripherie.
I can now use diagnostic option and I can see states of plc and module. What about those errors? I was sure that I’ve tried all but I didn’t. When i try to use scan option i get another error: The GSD file you will find here: This contribution was helpful to 1 thankful Users prmm21. Site Explorer Site Explorer. Have a look at the following FAQ and attached links: Am I missing CX-Server? Seeing the scan returns error with DTM version 1.
When I use “Test” option or prm1 go online I get errors: Follow us on Twitter Youtube. Product Support Services Forum mySupport. Hello Ariel; In your diagnostic messages a few stand out, at first glance ArielP 10!! I configured in S7 project the slave parameters. So many communication protocols to choose.
You need to be a member in order to leave a comment.
Hope this helps, Daniel Chartier. I made a diagnostic to de cp and appear this error: In the front of the module apeare that is the version 2.
CX-Configurator CJ1W-PRM21 connection problems. – Other Omron Software –
Edited 21 March by malyalewariat. Sign in Already have an account? The master prm2 me that the slave have a invalid response. Started by malyalewariat18 March prm21 cj1w bus profibus. I also programed the functions send and recv acording with the master configuration. Create an account or sign in to comment You need to be a member in order to leave a comment Create an account Sign up for a new account in our community.
I’m almost sure that this bosch unit provides profibus connection. I have no idea. When i try to use scan option i get another error:. Hello, the BF led blink in the omron master, the slave appear only with the led run.